Typhonix Coalescing pump is considered as a good alternative for pump A. As the OiW concentration is expected to be well above 200 ppm, this pump will have a positive effect on the separation efficiency of downstream produced water treatment equipment, as it will increase the droplet size of the dispersed phase. Also, this pump will improve the processes capability to handle an upset as the increase in droplet size is linked to the concentration of the dispersed phase. An increase in concentration will result in a further increase in droplet size, which will further improve the efficiency of the downstream treatment equipment. Typhonix Coalescing pump may also be considered as an alternative for Pump B. However, due to the low OiW concentration expected at this location (<200 ppm), the coalescing effect is expected to be limited. Typhonix Low Shear pumps are smaller and have reduced CAPEX compared to Typhonix Coalescing pumps. A Typhonix Low Shear pump is therefore considered more economically viable alternative for pump B.
CAPEX and OPEX considerations: Size and Weight
For obvious reasons no costs have been made available by the operator for the eccentric screw pumps. Evaluations for CAPEX and OPEX are therefore made based on the information available.
The size and weight of the respective eccentric screw pumps installed are given in Table 1. The data for the alternative Typhonix pumps selected for the applications is given in Table 2.
Table 1: Eccentric screw pumps
Based on the data from Tables 1 and 2, it can be concluded that the Typhonix pumps are both smaller and lighter than the eccentric screw pumps for both application A and B.
CAPEX and OPEX considerations: Mechanical and Process Safety
Eccentric screw pumps are a positive displacement pumps. These pumps require blocked outlet protection to prevent severe damage to the pump and/or piping in such an event. Piping systems with positive displacement pumps are normally fitted with a pressure relief valve or rupture disc assembly to prevent over pressurizing the system in a block outlet situation. This requires additional piping to reroute the liquid to a safe location. For this specific case, a pressure safety valve (PSV) is installed for both pumps with the necessary redundancy, valves, pipework, and heat tracing. The necessity to install a pressure protection system has an impact on CAPEX by increasing the amount of equipment, and on the OPEX by increased maintenance requirements.
The Typhonix Low Shear and Coalescing centrifugal pumps are both rotodynamic pump types. These pump types do not cause over-pressurization of the piping system in case of a blocked outlet, as the system normally is designed to withstand the maximal pump head. A pressure relief system is therefore not required.
Both the eccentric screw pumps and the Typhonix pumps will be supplied with variable frequency drives (VFD). The required minimum flow is within the operating range of the Typhonix pumps and minimum flow lines are therefore not required. Minimum flow lines are not recommended in low shear pumping applications as the size of the droplets of the dispersed phase is likely to be reduced due to shear forces in the minimum flow control valves.
CAPEX and OPEX considerations: Maintenance and Operation
No maintenance experience of the eccentric screw pumps is made available by the operator. The maintenance considerations discussed here are therefore gathered from operators having these pump types in use in similar produced water applications.
The main part of the eccentric screw pump exposed to wear is the stator, which is manufactured from a type of elastomer. Though this pump type is often reliably used to pump slurries, particles can cause significant wear to the stator when the liquid viscosity is low, as normally is the case for produced water applications. Several cases have been reported by operators where particles caused severe problems with to the stator lifetime. Issues with incompatibility of the elastomer with the produced fluids is also a known issue. The eccentric screw pump is dependent on a liquid to lubricate the area between the stator and the rotor. Running this pump dry will, therefore, cause significant damage to the stator.
Particles cause erosion in centrifugal pumps as well. This risk can be mitigated with correct material selection for the exposed parts. In addition, the Typhonix pumps will be operated at low rpm and with low liquid velocities inside the pump. This will further reduce the erosion rate of the pump internals. Furthermore, Typhonix pumps are built in accordance with API 610 meaning that the pumps are designed for a minimum service life of twenty years, excluding normal wear parts, and at least three years of uninterrupted operation.
In generally, noise isolation is not desired, as it is costly, bulky and reduces accessibility for inspection and maintenance. A requirement for noise isolation will, therefore, have a negative impact on both CAPEX and OPEX.
In the considered case, both Pump A and Pump B are installed in areas having an 85 dBA noise limitation. Both eccentric screw pumps required noise isolation in this case due to high noise levels of the gearboxes needed for these pumps. The added weight of the noise enclosures is 200 kg for Pump A and 175 kg for Pump B.
The Typhonix pumps do not require noise isolation for the considered case. The maximum noise level for the Coalescing pump, recommended for application A, is 66 dBA. For the Low Shear pump, recommended for application B, the maximum noise level is just 63 dBA. Both pump types, therefore, operate well below the area noise level limitation.
As highlighted in these articles and in the article on pump selection, all pump types discussed have their pros and cons. Selection of a pump requires a holistic view and not just focus on CAPEX. Is low shear required for the application or can you use a conventional single stage centrifugal pump? What is the added benefit of using a coalescing pump, could this reduce the number of produced water treatment stages? Maintenance and inspection frequency, redundancy, reliability, footprint, etc. are all important factors that need to be taken into account when selecting a suitable pump for the application.
For this specific case the Typhonix low shear and coalescing pumps are viable alternatives for the eccentric screw pumps. The benefits of this would be lower MTBF, no need for noise isolation or PSVs, and reduced footprint and weight. The coalescing pump additionally increases the systems capability to handle upsets and potentially reducing the number of treatment stages required to reach the discharge OiW target.